|Home||Search||Emissions||Pollutants||About the Database|
|LDEQ Accident Number
|Point Source(s)||Notes||Amount of Release|
|internal vapor combustor (source ID 1-91, EQT 0041)||Cause: Placid's internal vapor combustor (source ID 1-91, EQT 0041) was not operating upon an inspection conducted by an Environmental Engineer. The combustor was serviced upon notification. During the outage, only Placid's Tank Farm was routed to the combustor. Placid has no known reason why the combust or failed other than this was through a period of abnormally cold weather. VOC emission did occur as a result of this failure and the Benzene RQ was exceeded at 21lbs. Root cause was determined that operator error. Shut down alarm was not acknowledged.|
Notes: 3,205.63 lbs of VOC were released. Placid's Engineering and Terminal Departments are currently reviewing adding alarms to the terminal control system. In one part of the report, Placid states that the root cause of the failure was operator error. However, later they cite that the accident was the result of mechanical failure.
|Internal Vapor Combustor (source ID 1-91, EQT 0041)||Cause: During a review of trends on control equipment on 1/8/2014 it was noticed that Placid's internal vapor combustor (source ID 1-91, EQT 0041) was not operating. The combuster has the ability to control emissions from barge and/or truck loading from Placid's Tank Farm, however only Placid's Tank Farm was routed to the combustor during the outage. Placid has no known reason why the combustor failed other than abnormally cold weather. Placid has assessed the root cause as operator error as the shutdown alarm was not acknowledged.|
Notes: Placid's engineering and terminal departments are currently reviewing adding alarms to the terminal control system. Report states that actual engineering calculations will be maintained by Placid and are available for review upon request. Additionally, this report was filed in conjunction with another incident of the same DEQ number and State Police number. The cases to not appear to be related and occurred at different times with different materials discharged. No State Police Report was included for either case. Second case with the same DEQ and LSP number is included in database with DEQ#1532250 to differentiate them.