|About the Database
|LDEQ Accident Number
|Amount of Release
|Unit 59 North Flare
|Cause: The initiating incident was a pump seal fire in the Gasoline Desulfurization Unit (Unit 55). The fire was fueled by a leaking seal on the pump. Extinguishing the fire was delayed by inability to close an EIV on the suction side of the pump. This resulted in emergency shutdown of the unit. Two other events also occurred on this day including an upset in Sulfur Plant Unit 234 and a flame-out of the North Flare. Due to the fire and emergency shutdown of the Gasoline Desulfurization Unit, the Fluid Catalytic Cracking Unit cut feed, sending vent gas to the North Flare. Process vent gas was sent to the North Flare which increased the steam to the flare suddenly, snuffing the flare out.
Notes: PDF too large to upload (109 pages) To re-light the North Flare, steam was gradually decreased and natural gas was added to the flare gas to allow the two available igniters to relight the North Flare. Parts to repair the North Flare pilot system were already on order when this incident occurred. The North Flare was taken out of service when the parts were received and repaired on October 31, 2012. Spare pilot and igniter assemblies are now in stock so that repairs can be made in a timely fashion if an incident like this is to occur again. Total amount of pollutants released was 59438.44 lbs, but 90% was claimed to be efficiently burned off, resulting in 5943.59 lbs that were actually released. The reportable quantity for Highly Reactive Volatile Organic Compounds (HRVOCs) (100 pounds) was exceeded during the 24 hour period.
|leak from process line in U263 piperack
|Cause: On June 29, a pinhole leak was discovered in the LPG feedline from U212 to U222.
Notes: The line was purged with nitrogen and isolated for repairs. The Shift Emergency Response Team was activated and fire monitors were put on the leak to suppress any vapors. Reduced the U212 charge rate to minimize the leak. The line was isolated at battery limits in U222 and U212 to stop the leak. Once the investigation is complete, recommendations will be implemented.
|U212 Platformer unit
|Cause: On May 22, a small leak and hydrogen fire was observed on the 48" flange on the process piping going from cell 1 of the Unit 212 Charge Heater to Reactor #1. The leak was pinhole sized in width and no larger than 1" around the circumference of the flange.
The emission point involved was a flange on a process line in the U212 Platformer unit.
Notes: Steam was applied to the flange to extinguish the flame and the flange was hot bolted to secure the leak. Once the investigation is complete, recommendations will be implemented. An additional followup on 10/23/13 corrected the initial followup report's emissions data regarding greenhouse gas releases.