|Home||Search||Emissions||Pollutants||About the Database|
|LDEQ Accident Number
|Point Source(s)||Notes||Amount of Release|
|FLARE - Alkylation Feed Preparation Unit||Cause: The Methyl Tertiary-Butyl Ether Unit was converted to an Alkylation Feed Preparation Unit (AFP). The AFP was beginning its initial start up. As the level in one of the towers increased, steam was added to the reboiler to begin producing overhead product. During this time, the safety valves on the tower began relieving to the flare system, which resulted in the reported flare. During the conversion of the unit the overhead pressure meter was reranged in the field, but was no reranged in the control room. Due to this oversight the operator believed he was at a significantly lower pressure and did not immediately discover that the safety valves on the tower had lifted to the flare system. The calculations automtically completed by the flare system|
Notes: The cause of the accident is listed as preventable in the company's report, but there is no explanation whatsoever as to why it was preventable - that section is blank. The only remedial measure listed is that the pressure meter range was corrected in the control room. The letter to LDEQ states that reportable quantities of nitrogen oxide and butenes were exceeded.
|MTBE Unit Exchanger E-557||Cause: MTBE Unit Exchanger was discovered to leaking into the condensate system causing vapor to flash off. The failure mechanism causing the leak in the exchanger is listed as unknown.|
Notes: Incidents 06-00380, 06-00401 occurred simultaneously on January 19th and on Jan. 20th 06-00406 occurred, overlapping with the first two. The reportable quanitites for highly reactive volitile organic compounds and flamable vapors were exceeded whenthe emissions from these three events were summed over the first 24 hour period beginning with the initiantion of the rlease from the No. 2 Powerformer Unit. With regard to the 24 hour period beginning with the release at the MTBE Unit, there were nportable quanity exceedances for this period of time. The emissions limit exceeded the reportable quanitity threshold only during the time when all three incidents were taking place simultaneously. The mortar in T-4X will be replaced with a Furan re
|Leak/feed line leak||Cause: Corrosion/corrosion leak occurred through a 3/8 hole on the #2 feed inlet pip|
Notes: The tower that the corroded pipe led to was shut down and filled with water to stop residual hydrocarbon vapors from leaking out of the hole. The hole was plugged.An engineered leak box was installed on the line.
|No Information Given||Cause: Leak occurred, but no information provided about the cause.|
Notes: Release is BRQ. Secured leak and will de-pressurize line then replace pipe. LABB does not have access to the LDEQ incident report.