|Home||Search||Emissions||Pollutants||About the Database|
|LDEQ Accident Number
|Point Source(s)||Notes||Amount of Release|
|alkylation unit||Cause: |
Notes: water was sprayed on the vapor cloud to mitigate hazards from the release. Upstream and downstream block valves had to be closed to stop the leak; this was not preventable because the gasket failed- it was an appropriate gasket for the service
|Leak/feed line leak||Cause: Corrosion/corrosion leak occurred through a 3/8 hole on the #2 feed inlet pip|
Notes: The tower that the corroded pipe led to was shut down and filled with water to stop residual hydrocarbon vapors from leaking out of the hole. The hole was plugged.An engineered leak box was installed on the line.