|Home||Search||Emissions||Pollutants||About the Database|
|LDEQ Accident Number
|Point Source(s)||Notes||Amount of Release|
|F-485 Motor Alkylate Tank||Cause: The incident was due to the inadvertent landing of the external floating roof of tank F-485 onto its legs due to low gauging. The F-485 motor alkylate tank was low gauged and set on its legs, causing two 2" vents to open to the atmosphere for a duration of 12 minutes.|
Notes: No information given.
|DU-5 Naptha Stripper Reboiler [E-1004]||Cause: A leak in the weld of a pipping elbow of the DU-5 Naptha Stripper Reboiler caused by internal corrosion on the reboiler.|
Notes: RQ. Reportable quantities were exceeded for 8 chemicals including Ethane, Methane, Toulene, and n-Hexane. Refinery report states that "immediately following discovery of the leak, the site's emergency response team was activated and the naphtha stripper was blocked in and depressurized."