|Home||Search||Emissions||Pollutants||About the Database|
|LDEQ Accident Number
|Point Source(s)||Notes||Amount of Release|
|WWTP Outfall 110||Cause: see notes. WWTP became upset due to recent high levels of contaminants entering the feed unit|
Notes: Sheen of approx. 300 sq ft. Under investigation.
|WWTP Clearwell||Cause: WWTP in upset condition causes release of effluent through Outfal 110|
Notes: CRLLC immediately shut down discharge pumps and diverted the WWTP Clearwell effluent back to the API. The sheen dissipated immediately. CRLLC is performing additional visual and chemical analysis of the feed to the API. Once a shift CRLLC is collecting and analyzing samples and has reduced the drain rate of the feed to the WWTP.