|Home||Search||Emissions||Pollutants||About the Database|
|State Police #||11-00823|
|Pollutant||Duration||Point Source||Greenhouse Gas||Criteria Pollutant||Ozone forming chemical||Amount of Release|
|Kerosene||30m||#3 Cargo Sump||NO||NO||YES||63.0 gallons|
|Volatile Organic Compounds (VOCs)||30m||#3 Cargo Sump||NO||NO||YES||635.0 pounds|
|Benzene||30m||#3 Cargo Sump||NO||NO||YES||0.1 pounds|
Accident Classified As:
Unauthorized discharge report states that kerosene flowed out of the concrete basin surrounding #3 Cargo Pump House Sump PPS-29, onto the ground underneath the piperack west of PPS-29 and into the concrete rainwater catch basin southwest of PPS-29. The operator left D-1216 draining unattended. The radar span on PPS-29 was not set properly.
The operator left D-1216 draining unattended. The radar span on PPS-29 was not set properly
Sump level was pumped down. The radar span on PPS-29 has been adjusted. The company will consider installing redundant radar level indication on PPS-29. They will consider scheduling annual preventive maintenance and testing on PPS-29 level control system as well as a low level alarm to PPS-29.
Connect With Us: