|About the Database
|LDEQ Accident Number
|Amount of Release
|Cause: Three events occurred within 24 hours of one another at the ExxonMobil Baton Rouge Chemical Plant. Two are reported in this report (LDEQ #107433), the other is reported separately (LDEQ #107421). In this incident (107433), a furnace tube leaked into convection section of H-furnace and caught fire. The tube leak occurred as a result of the incident described in report #107421.
At approximately 5:56 PM on July 21, 2008, the charge gas compressor at the Olefins unit shut down when several processing cards in the gas turbine control system failed. When the compressor shut down, four furnaces automatically shut down and the gas in the furnaces was evacuated to the flare system. One of the remaining three furnaces was subsequently shut down while the remaining two furnaces continued to operated at 50% rates in order to maintain stable unit operations, which resulted in additional flaring for the duration of the event. The high rate of gas to the flare system resulted in the #25 flare smoking for 2 hours and 17 minutes.
When the Olefins unit shut down, steam was introduced into the furnaces to displace the hydrocarbon feed to reduce flaring emissions. At 12:20 PM on July 22, 2008, while the H furnace was in the process of starting up, a leak was discovered in the convection section of the furnace. To stop the leak, water was introduced into the leaking pass of the furnace to displace the hydrocarbon feed. It is believed that the leak developed when steam was introduced into the furnace.
Tube leaked into convection section of H-furnace and caught fire.
Notes: This incident is the result of the incident #107421 (see comments under that incident). Immediately after the incident began, five of the seven furnaces at the Olefins unit were shut down. Excess gas was sent to flare system. Water was introduced into the leaking furnace pass to displace the feed and prevent uncombusted hydrocarbons from leaking into the atmosphere. Concerning subsequent preventative actions, the failed processing cards were replaced. The H furnace was taken out of service to be inspected for leak location and repairs will be completed as necessary. Used water in the tube to eliminate the burning material. Flammable gass consisted of mainly Butane.
|SACC unit LTO1
|Cause: A leak developed in a fifty four inch overhead pipe at the SACC Unit LT01.
Notes: There is approximately 5 lbs per square inch (psi) or pressure on the pipe. The insulation of the pipe was removed to identify the source. Pictures included of the plug of the pipeline due to the hole and a view of the repaired line. On the incident report form it says that the initial report said that RQs might be exceeded, but that none were exceeded.