|Home||Search||Emissions||Pollutants||About the Database|
|LDEQ Accident Number
|Point Source(s)||Notes||Amount of Release|
|flare||Cause: Crude unit upset resulted in intermittent flaring from 3 different process vessels.|
Notes: Reduced rates and shutdown isomerzation and LRU unit to minimize flaring until flow rates could be stabilized. Same issue as the release on the previous day.
|flare||Cause: Crude unit upset caused flaring from 3 different process vessels.|
Notes: Reduced rates and shutdown isomerzation and LRU unit to minimize flaring until flow rates could be stabilized.
|FLARE - FCCU flare||Cause: "Loss of power in Complex II caused operating and utility units to shutdown. This even resulted in flaring from the FCCU flare" Due to the loss of power, the complex II steam producers shut down, therefore the flare steam assist was lost. This resulted in smoking flares. This released the following chemicals: SO2, H2S, NOx, VOC, Hexane, and 1,3 Butadiene. FLARE.|
Notes: A power feed was connected from Complex I to Complex II, and boilers were restarted to produce steam to assist the FCCU flare, and shutdown procedures was continued. No LDEQ report. Refinery Letter only.