|Home||Search||Emissions||Pollutants||About the Database|
|LDEQ Accident Number
|Point Source(s)||Notes||Amount of Release|
|179 Thermal Hydrodealkylation Unit H1 Heater||Cause: The outlet flanges located on the outside of the convection section of the 179 Thermal Hydrodealkylation Unit H1 Heater leaked toluene onto surrounding hot surfaces. The toluene ignited causing a small fire at the flanges. It is suspected that the heavy rainstorm may have caused the metal to contract creating the slight opening at the flange faces.|
Notes: Fire was extinguished using fire water. Unit was shutdown and de-pressured.