|Home||Search||Emissions||Pollutants||About the Database|
|LDEQ Accident Number
|Point Source(s)||Notes||Amount of Release|
|No LDEQ Reported|
|Tank 164||Cause: Pump seal failed on tank 164 and leaked onto electrical heat trace. Electrical ignition of heated oil started a fire and plant personnel extinguished the flame.|
Notes: Fire extinguished by plant personnel. No injuries or offsite impacts. No specific remedial action taken.
Connect With Us: