|Home||Search||Emissions||Pollutants||About the Database|
|LDEQ Accident Number
|Point Source(s)||Notes||Amount of Release|
|Flare||Cause: There was a problem creating back pressure at the compressor, which caused a valve to lift and release hydrogen into flare header.|
Notes: The hydrogen release was BRQ and lasted 15 minutes. The total amount of hydrogen released was 6878 lbs.
|Hydrogen: 6,878.0 pounds|
|Relief valve on pipeline||Cause: The compressor recyclers did not respond quickly enough, so increased pressure in the pipeline caused the relief valve to pop, releasing hydrogen to the air.|
Notes: The release was reported as being secured immediately, and 2.19 lbs. of hydrogen were released, which is below reportable quantity. The State Police Report indicates that a 7-day report was promised.
|Hydrogen: 2.2 pounds|