|Home||Search||Emissions||Pollutants||About the Database|
|LDEQ Accident Number
|Point Source(s)||Notes||Amount of Release|
|Pump, Tank Farm Area 18||Cause: Small pump fire and spill in the tank farm area 18.|
Notes: The spill was cleaned up.
|FLARE - FCCU flare||Cause: "Loss of power in Complex II caused operating and utility units to shutdown. This even resulted in flaring from the FCCU flare" Due to the loss of power, the complex II steam producers shut down, therefore the flare steam assist was lost. This resulted in smoking flares. This released the following chemicals: SO2, H2S, NOx, VOC, Hexane, and 1,3 Butadiene. FLARE.|
Notes: A power feed was connected from Complex I to Complex II, and boilers were restarted to produce steam to assist the FCCU flare, and shutdown procedures was continued. No LDEQ report. Refinery Letter only.
|Crude Unit Flare and FCCU Unit Flare||Cause: Extreme cold front moving through area with heavy rains and "tomadic" winds. Power trip upset that resulted in unusual flaring. During severe weather and winds, power feeding the plant from the utility company tripped off, shutting down the entire refinery.|
Notes: Safety reliefs vented to the flares as designed to control the upset. Permit limits were exceeded, but no reportable quantities were released. Flares smoked for approximately 5 minutes in compliance with Title V permit conditions.
|FLARE: FCCU||Cause: FCC unit started up after 2 weeks of planned maintenance. Relief valves opened to flare when weight gas compressor for FCCU malfunctioned. Two odor complaints received by LDEQ connected to this accident. Starting unit for the wet gas compressor on the FCCU malfunctioned. 2 Citizen Complaints included: 135203 and 135197|
Notes: Report states that Title V permit limits were exceeded. A site visit was made on 11/15/2011. Unit started up after two weeks of maintenance. Unauthorized Discharge Notification Report received 11/22/11. Report states that the maximum hourly permit limit was exceeded for hexane but no reportable quantities were exceeded. they did not realize until the next morning that RQ was exceeded.