|Home||Search||Emissions||Pollutants||About the Database|
|LDEQ Accident Number
|Point Source(s)||Notes||Amount of Release|
|exchanger 05-1313||Cause: Pinhole leak from exchanger, 05-1313, caused a release of naphtha to the coker unit pad.|
Notes: the exchanger was isolated, and contents were directed to the oily water sewer.
|FCCU wet gas compressor first stage||Cause: A loose wire in a satellite building caused the Fluid Catalytic Cracking Unit (FCCU) wet gas compressor first stage spillback to open, which led to high fractionator pressure. The safety instrumented system (SIS) tripped the FCC unit on high fractionator pressure. During the FCC unit startup, the debutanizer pressured up and had to be vented to flare due to lack of heat in the upstream stripper reboiler (heating medium is BPA from the fractionator) which sent ethane to the debutanizer.
The flaring event due to the FCCU Shutdown began on June 7, 2014 at 14:37 hours and stopped on June 7, 2014 at 15.48 hours for a duration of 70 minutes. The flare event due to the FCCU startup began on June 7, 2014 at 18:21 hours and stopped on June 7, 2014 at 20:18 hours for a duration of 117 minutes. The total duration of the flaring was 187 minutes.|
Notes: The SIS system reacted as designed to shutdown the FCCU due to the opening of the compressor spillback valve. During FCCU startup the operating procedure was followed to minimize emissions to the extent possible. An incident investigation will result in recommendation items designed to prevent the recurrence of this event.