|Home||Search||Emissions||Pollutants||About the Database|
|LDEQ Accident Number
|Point Source(s)||Notes||Amount of Release|
|B-12 FLARE||Cause: Outage of JC-1B recycle Hydrogen Compressor at Unicracker Unit.|
Notes: Claims emission was below RQ
|B-12 Flare||Cause: flaring of excess hydrogen during outage of JC-1B recycl Hydrogen Compressor at Unicracker Unit|
Notes: Claims emission was below RQ. Shut unit down and repaired compressor
|A Reformer Unit||Cause: piping leak at the A-Reformer Unit|
Notes: No Information Given
|B-11 Flare (EIQ No. 3(XXII)4) and (ID No. EQT 350)||Cause: pilot outages of B11 Flare - malfunctioning pressure regulator on nat. gas to pilots|
Notes: Emissions exceeded RQ of 100 lbs. operator checks on gas line pressure downstream; development of a routine schedule for maintenance checks on the regulator; instrument group has repaired pressure regulator that malfunctioned.
|isom unit||Cause: Flange leak in the Isomerization unit--no further details
no DEQ report in this file|
Notes: "Citgo personnel are making repairs", no specifics given.
|C103 Exchanger||Cause: Fire from hydrogen leak from a bad gasket at C103 exchanger--burned about 10min.|
Notes: Line depressurized to B9 flare and unit shut down. "Plant performed perimeter monitoring and had no readings." No Refinery letter included. Only LDEQ verbal report.
|B12 flare||Cause: The JC 1C Compressor over-pressurized causing relief valve to open to B-12 flare.|
Notes: No information given
|B-12 flare||Cause: Swapping out compressors, overloaded system, valve released to flare|
Notes: no information given
Connect With Us: