|Home||Search||Emissions||Pollutants||About the Database|
|LDEQ Accident Number
|Point Source(s)||Notes||Amount of Release|
|Cooling Tower 1 and 2||Cause: of heat exchanger tubing that releases ammonia into the hot water that goes to the cooling tower|
Notes: Leak occurred at York Ammonica System C-52A Condenser at C-4 Recovery Unit. Leaking tubes plugged and all tubes in heat exchanger are Seakaphen coated to resist corrosion. EXTREMELY HAZARDOUS.
|B-7 Flare||Cause: shut down for planned turnaround of York System and parts of the C-4 Recovery Uni|
|storm water sewer||Cause: Source of hydrogen sulfide and ammonia odors were detected in the vicinity of the storm water main lateral is under investigation.|
Notes: Investigation and closure letter are to be delivered by 5-15-09.
Connect With Us: