|Home||Search||Emissions||Pollutants||About the Database|
|LDEQ Accident Number
|Point Source(s)||Notes||Amount of Release|
|Tank Farm||Cause: Unknown|
Notes: Inspected floating roof seals, cleaned the area with vacuum truc
|Tank 32||Cause: Tank overfilled|
Notes: Vacuum truck and removal of the contaminated soil
|tank farm||Cause: Approximately 700 barrels of naphtha were discharged from the roof of tank 58. The gauging system had failed and manual readings were not taken.|
Notes: Stopped flow into tank, foamed product,removed naphtha from within diked area.
|Platform Unit Charge Heater #1 (EQT 250)||Cause: Rupture of tube in heater fire box. No 1 Platformer charge heater (EQT 0250) exceeded opacity >20% for approximately 20 minutes. The unit was turned off and cooled.|
Notes: Feed and fuel into heater were removed, steamed out and water was sprayed to cool. The report states that the heater tubes will be repaired to proven recurrence. A field interview was conducted on 5/23 and photos were taken which are included in the pdf file. At the time of the inspection, a steam plum exhaust from the heater stack due to water sprayed on to the heater to cool the unit.
|No information Given|
Connect With Us: