|Home||Search||Emissions||Pollutants||About the Database|
|State Police #||N/A|
|Pollutant||Duration||Point Source||Greenhouse Gas||Criteria Pollutant||Ozone forming chemical||Amount of Release|
|Crude Oil||Tank 13||NO||NO||NO||84.0 gallons|
Accident Classified As: Reportable Quantity
Crude oil was observed leaking from a buried section of piping which fills Tank 13. Estimated to have released between 2-4 barrels.
Placid employs good engineering practices in accordance with industry standards for corrosion protection and mechanical integrity, including cathodic protection.
Placid placed a temporary clamp on the leak, left the line exposed for observation, and will be replacing the section of piping in the near future. Vacuum trucks, booms, and absorbent materials were used to clean the area. Contaminated soil removed and placed in roll-off boxes. A "French Drain" with a standpipe has been installed in the affected area to capture any residual oil. At this point, Placid is unsure of the duration of the discharge due to the small size of the hole in the piping underground. In a follow up report on 4/15/2014 it is stated that a report on 4/15/2013 found that no groundwater was encountered by this spill and requested LDEQ to approve of the use of "French drains" for collecting any residual oil that could not be removed. Not all impacted soil was removed as various structures in the area prevented the removal of all soil. The use of "French drains" was approved by LDEQ in a document dated 6/20/2013. As the time of the follow up report (4/15/2014), no additional oil had been encountered in the "French drains" and they had been removed and the site has been returned to its pre-incident condition.