|Home||Search||Emissions||Pollutants||About the Database|
|State Police #||093118|
|Pollutant||Duration||Point Source||Greenhouse Gas||Criteria Pollutant||Ozone forming chemical||Amount of Release|
|Diesel Fuel||1 h 30 m||Sump pump||NO||NO||YES||BRQ|
|Kerosene||1 h 30 m||Sump pump||NO||NO||YES||BRQ|
|#6 Oil||1 h 30 m||Sump pump||NO||NO||NO||BRQ|
Accident Classified As:
A delay in the automatic start-up of sump pump 839 on Placid's south dock allowed oily material to back up into secondary containment. A previously unknown crack in the secondary containment curb allowed material to seep out and cause a sheen.
No information given
Automatic switches were replaced, and the pump was reset. Also the crack was repaired.